1.0 MX-3000+ - GENERAL
1.1 MX-3000+ is a direct retrofit kit specifically designed for facilities with existing Electronics Diversified Inc. (EDI) or Copper MX Series dimmer rack(s) requiring new, reliable and cost-effective control electronics. MX-3000+ is designed to upgrade existing dimmer installations to current dimming technology while maintaining the existing rack, modules and wiring infrastructure. Designed for pin-to-pin compatibility with the MX Series OEM factory dimmer control wiring, installation is both fast and easy. Facilities can upgrade to this state-of-the-art technology in minutes. The MX-3000+ is ETL compliant with UL 508 and CSA 22.2 safety approvals.
1.2 MX-3000+ shall employ a unique "lamp warming" feature that extends lamp life substantially by limiting the in-rush current from the dimmer to cold lamp filaments by up to 70%.
1.3 An LCD user interface for ease of set up and monitoring. All programming shall be via a user-friendly, intuitive and self-prompting menu structure. No PC or special OS software by others will be required.
1.4 Modular design of the unit shall make any potential service requirements fast and easy.
1.5 Dimmer control outputs shall be designed for precise and reliable control of the existing MX Series dimmer modules. It shall never be necessary to adjust ramp circuits for proper dimmer output.
1.6 The MX-3000+ shall accept dual independent DMX 512-A digital data protocol inputs allowing industry wide compatibility with modern control consoles. Both DMX inputs shall be independently opto-isolated from all other control circuitry, as well as from the DMX output ports. An internal protocol manager shall allow priority management, offset start addressing or merging of both DMX inputs. It shall be possible to "patch" any of the 96 dimmer (PWM) outputs to any DMX A or DMX B input channel.
1.7 An infrared LED link shall be provided on the control module face panel. This interface will permit hard copy printouts of all programmed data via an optional hand held infrared printer.
1.8 Rack thermal protection shall be employed to interface with the existing dimmer module over-temp sensors and wiring. An active over-temp input from any dimmer shall illuminate a red warning LED. An internal MX-3000+ temperature of 65°C shall immediately disconnect of all dimmer control outputs.
2.0 CONTROL PCB
2.1 The MX-3000+ control electronics shall be capable of controlling up to 96 dimmers in the MX Series dimmer cabinet. Advanced state-of-the-art voltage regulation hardware and software will ensure >1% all dimmer outputs. The MX-3000+ will operate with a voltage input range of 85-264VAC at 50 or 60Hz.
2.2 The MX-3000+ shall be capable if memorizing and storing up to 20 presets in the form of a DMX "snapshot" or individually programmed via the keypad. Scene playback shall be seamless on loss of DMX as well as allowing high resolution fades between all 20 scenes. Each scene shall have a selectable fade time from 0-99 seconds.
2.3 The DMX512 input ports shall accept two independent sources of DMX512 data protocol simultaneously from the system control console(s) or architectural control unit(s). The DMX inputs shall comply with USITT DMX512-A (ANSI E1.11 - 2008), standard protocol for digital data control.
2.4 It shall be possible to assign (patch) any dimmer control signal to any module position in the cabinet, thereby allowing dimmer modules of any rating to be used in the same cabinet.
2.5 MX-3000+ will offer compliance with the International Energy Agency's "One Watt Initiative" on stand-by power requirements (please refer to U.S. Executive Order #13221). Standby power on the MX-3000+ shall not exceed 1 Watt.
2.6 The MX-3000+ shall allow "back up" of all system configuration data. All data shall be protected from power failure by EEROM for a minimum of 100 years.
2.7 The MX-3000+ shall contain a removable memory dongle to facilitate remote or off site back up of all system configuration and ease of future firmware upgrades. MX-3000+ swaps, if necessary, will be easy and fast with no loss of rack programming or system parameters.
2.8 The MX-3000+ shall accept up to 4 (four) analog inputs with the ability to be assigned to any of the 96 outputs in the system. Each analog input shall be selectable as either "Normal" mode (0-10VDC input) for dimmed applications or "Load Shed" mode (5VDC trigger) for power management interface to building management systems (BMS). The analog inputs shall function in a pile-on or HTP mode with the DMX control signal.
2.9 Dedicated dry contact inputs shall be provided for BMS, HVAC, security and fire alarm. Active security input shall "flash" any programmed dimmer outputs to a selectable level at a rate of 1Hz. Active fire alarm input shall bring any programmed dimmers to a selectable level and override all incoming control data.
2.10 Each individual dimmer in the dimmer rack shall be capable of being assigned one of four dimmer curves: incandescent square law curve, direct curve, linear curve, or non-dim. Non-dim threshold shall be adjustable in 10% increment from 10% through 100% with a 5% hysteresis.
2.11 The face of the MX-3000+ shall include an LCD display and momentary push buttons for function select, parameter setting and feature monitoring. All programming shall be via a user-friendly, intuitive and self-prompting menu structure. It shall not be necessary to use a PC or any external programming devise to configure or set-up any function of the MX-3000+.
2.12 The MX-3000+ shall employ the "system-on-a-chip" advanced "3000 Series" digital technology. Such electronic circuitry shall permit real time signal monitoring and status LED indication to allow easy setup and remote troubleshooting. The MX-3000+ shall permit configuration/monitoring of the following within the MX Series dimmer rack:
2.13 The MX-3000+ face panel shall include a green LED indicator for power supply and microprocessor status. The LED, when illuminated, shall indicate normal operation, and when flashing shall indicate a hardware fault. A power supply or power failure, shall cause the LED to extinguish.
2.14 The MX-3000+ face panel shall include three green LED's for phase detect and two yellow LED's for data receive indication. Loss of accurate phase detect signal and/or invalid DMX512 data shall cause the corresponding LED to extinguish.
2.15 The MX-3000+ face panel shall include two red LED's for active alarm status or dimmer rack over temperature. Active inputs shall cause these cause the corresponding LED to illuminate.
2.16 A reset push-button shall be included on the face panel of the MX-3000+. Resetting the unit, whether by the reset button or power-up shall not affect any stored parameters or presets, and dimmer outputs shall automatically return to their former status.
2.17 It shall be possible to "Lock" and "Unlock" the programming keypad of the MX-3000+ in order to protect all programmed system data.
2.18 The MX-3000+ shall incorporate fan control circuitry to control the existing MX Series rack fans and is designed to allow for an additional five (5) minutes of air evacuation from the dimmer cabinet with loss of input control signal.
2.19 All printed circuit boards (PBC's) shall be FR4/G10 with a UL 94V-0 Flame Class Rating.
2.20 The entire assembly shall be ETL compliant with UL 508 and CSA 22.2 safety approvals.
Specifications subject to change without notice.
Copyright © 2022, Johnson Systems Inc., All Rights Reserved